Socomec ATys 2Pole, Single Phase, 125Amp, Automatic Transfer Switch
Mounted inside an IP55 Wall Mounted Enclosure
Once Mains Failure occurs, ATS sees a loss of supply to it’s primary source and will send a Remote Start signal to the Standby Generator. Generator will run up to speed and supply the secondary side of the ATS. Once the ATS sees a healthy secondary supply from the Standby Generator, it will automatically switch the building load onto Generator Power.
On restoration of the Mains Supply, the ATS sees a healthy primary source again and monitors it for a set period of time. Once this time has lapsed, the ATS will transfer the load back to the primary source of power (Mains/ESB).
The Generator will now continue to run on offload for a set period of time to cool the engine down. The Generator will then switch off and the system will return to Automatic mode again and remain on standby until the next mains interruption
Fully Automatic with Manual Over-ride Key should it be needed